Last previous edition approved in as D – Adopted as a joint ASTM/ IP standard in 2 For referenced ASTM standards, visit. Test Report of Foaming Characteristic (ASTM. D) and Air Release (ASTM D ). Test Report of Foaming Characteristic (ASTM. D) and Air Release. ASTM D Standard Test Method for Air Release Properties of Hydrocarbon Based Oils. standard by ASTM International, 10/01/ View all product.
|Published (Last):||5 November 2014|
|PDF File Size:||17.12 Mb|
|ePub File Size:||3.10 Mb|
|Price:||Free* [*Free Regsitration Required]|
NOTE 2—By agreement between the customer and the laboratory, the oil may be heated at other temperatures. However, the precision at these different temperatures is not known at present.
Interchanged parts may be used so long as the resultant test vessel conforms to the stated dimensions. Send your message to this supplier. It is the last photo. Air from a cylinder or a nonpulsating pump may be used. NOTE 8—Oil misting occurs during blowing. Care shall be taken to avoid restricting the air path with the thermometer bulb or any adapter used. Individual reprints single or multiple copies of this standard may be obtained by contacting ASTM at the above address or at phonefaxor service astm.
This standard is subject to revision at 3d427 time by the responsible technical committee and must be reviewed every?
Historical Version s – view previous versions of standard. NOTE 6—Previously, chrome sulfuric acid was used in this procedure.
Air Release Value Apparatus ASTM D3427
This may take about 20 min. If the loss causes any part of the sinker to be exposed, discontinue the test and repeat, using a sample that is 10 mL larger than previously used. Request a custom order and have something just for you!
Work Item s – proposed revisions of this standard. It is used to test the ability of turbine, hydraulic, and gear oils to separate entrained air.
NOTE 12—For some applications, the shape of the air release time curve may be required. A coil of copper tubing immersed in the circulating bath see 6. Warning—The use of glass vessels with glass host?
ASTM D3427 Lubricating Oil Air Release Value Test Device (TP-0308)
The significance of this test method has not been fully established. Digital display temperature controller. Other test methods for example, Test Method D have demonstrated acceptable, statistically equivalent results when Nochromix or Micro is used to replace sulfuric chromic acid for cleaning.
If the astmm time in the reservoir is too short to allow the air bubbles to rise to the oil surface, a mixture of air and oil will circulate through the lubricating oil system.
It is the responsibility of the user of this standard to establish appropriate safety and health practices and determine the applicability of regulatory limitations prior to use. Users of this standard are expressly advised that determination of the validity of any such patent rights, and the risk of infringement of such rights, are entirely their own responsibility.
No other units of measurement are included in this standard. Allow the sample to reach the test temperature. Link to Active This link will always route to the current Active version of the standard. This test may not be suitable for ranking oils in astn where residence times are short and gas contents are high.
NOTE 3—The application of thermal asfm to the pipework carrying the heated compressed air is recommended. NOTE 16—The precision statement was developed using 1.
ASTM D – 15 Standard Test Method for Air Release Properties of Hydrocarbon Based Oils
A number in parentheses indicates the year of last reapproval. Your comments are invited either for revision of this standard or for additional standards and should be addressed to ASTM International Headquarters. Back pressure in excess of a gage pressure of 70 kPa 10 psi can be generated when the bath medium is pumped at the required rate; this can cause fracture of the glass or slippage of the hose connections.
Originally approved in China soxhlet apparatus China flash point apparatus China thermal conductivity apparatus. Attach the wire to the beam and maintain a distance of 10 6 2 mm between the bottom of the sinker and the bottom of the zstm vessel. NOTE 5—The application of thermal insulation to the pipework carrying the heated bath?